The ASTM E (Standard Test Method for Water Penetration of Exterior Windows, Skylights, Doors, and Curtain Walls by Uniform Static Air Pressure. Imison. John H. Waskow, P.E.. Architectural Testing, Inc. Test Method: ASTM E , Test Method for Water Penetration of Exterior Windows, Curtain Walls. Purchase your copy of ASTM E – 00() as a PDF download or hard copy directly from the official BSI Shop. All BSI British Standards.
|Published (Last):||9 May 2004|
|PDF File Size:||15.20 Mb|
|ePub File Size:||15.93 Mb|
|Price:||Free* [*Free Regsitration Required]|
Building Diagnostics Group, Inc. This test method exclusively utilizes a uniform static air pressure difference.
Water Penetration Field Testing
The AAMA describes steps for calculating the approximate differential air pressures the specimens experienced during actual wind driven rain events. Referenced Documents purchase separately The documents listed below are referenced within the subject standard but are not provided as part of the standard.
Failures during quality assurance new construction testing can result in unnecessary delays that impact your bottom line. This allows us to not only properly test fenestrations on new construction projects, but also pinpoint the cause of any test failures and provide accurate recommendations to achieve successful testing results.
ASTM International – Standard References for ASTM E – 00()
The ASTM E Standard Test Method for Water Penetration of Exterior Windows, Skylights, Doors, and Curtain Walls by Uniform Static Air Pressure Difference is a testing standard that describes the procedures to determine the water penetration resistance of windows, curtain walls, skylights, and doors when water is applied using a calibrated spray apparatus while simultaneously applying uniform static pressure to opposite sides of the test specimen.
ASTM E references the following documents: The reviewing of project documents for the building. Analyzing the data and establishing a cause and effect relationship between wall characteristics and the observed leakage. Specifically excluded from this field check method is the testing of operable components such as operable window and doors. This specification is for quality assurance testing only. BDG utilizes professional testing equipment that is calibrated to each specific testing standard for accurate results.
For specific hazard statements, see 7. ASTM states that the field test may be made at the time the window, skylight, curtain wall or door assemblies are initially installed.
ASTM E331 – 00(2016)
Conducting the investigative testing to verify and extend hypotheses arrived at during the document review and inspection portions of the investigation using controlled and reproducible procedures. This field water check method is not intended to test the rated or specified water performance representative of a wind driven rain event.
This differs greatly from the AAMA and AAMA field testing procedures that are intended for evaluating newly installed fenestration products or quality assurance testing. Most generic specifications call for a minimum testing pressure of 6. It can only be utilized prior to the issuance of the building occupancy permit and no later than six months after the installation of the fenestration product.
Historical Version s – view previous versions of standard.
This standard is utilized for either field quality assurance testing or forensic testing. The calibrated spray apparatus spray-rack system delivers water to the test specimen at a rate of 5. This standard is utilized for laboratory or interior mock up testing only. BDG has extensive knowledge of most building systems and specializes in forensic water intrusion investigations.
These factors should be fully considered prior to specifying the test pressure difference to be used. If you are looking for a reputable second or third-party testing company to perform accurate professional testing, provide concise reports, and help you through the entire process, contact BDG today. Read more about what our customers have to say In service, the performance will also depend on the rigidity of supporting construction and on the resistance of components to deterioration by various causes, vibration, thermal expansion and contraction, etc.
It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. This starts with a clearly defined sequence r331 activities that SITC follows during a investigation: In applying the results of tests by this test method, note that the performance of a wall or its components, or both, may be a function of proper installation and adjustment.
This test method does not address these issues. The atsm of the design concept to determine if any water resistance performance requirements were specified for the wall. The main objective of forensic water testing is to identify the leak paths through the simulation of the weather events that produced the reported leakage. There are two different procedures listed for the test method.
The water spray system has nozzles spaced on a grid to deliver water so that the test specimen is wet uniformly, includingthose areas vulnerable to water penetration.
Give us a call to discuss your next project. Procedure B is a cyclic static air pressure difference.
Water that penetrates the assembly, but does not result in a failure as defined herein, may have adverse effects on the performance of contained materials such as sealants and insulating or laminated glass. MISSION Professional services based on accurate information that helps you or your company make the right decision regarding your project or asset.
Specifically excluded ashm this specification are windows, glass doors and skylights.